Intumescent Firehood - large
Intumescent firehood to be used to reinstate the fire integrity of ceiling. Rated at 1 hour fire protection. Fire hood - Please refer to fire boxing and fire hood installation sheet. Only to be used where fire boxing is not possible. Requires a minimum recess depth of 150mm. When using a fire hood clear away insulation materials and debris from around the fire hood by 100mm from the edge. Insulation materials to be removed clear above the fire hood. Transformers must be pushed away from the outside of the fire hood by a minimum of 100mm. Please read our Fire Hood Policy and Disclaimer before purchase or use. John Cullen Lighting accepts no responsibility for incorrectly specified or installed Fire Hoods that may cause the luminaire to overheat and could possibly lead to fire.